Welcome to the Molson Coors Lighting Test Records
Carry out monthly emergency lighting test and inspection as per BS5266-1to all sites as per your specification.
Switch each luminaire and each internally illuminated exit sign to emergency mode so it uses the battery. This simulates a failure of the supply of the normal lighting and continues for a period sufficient to ensure that each lamp is illuminated.
At the end of this test period, the supply to the normal lighting should be restored and any indicator lamp or device checked to ensure that it is showing that the normal supply has been restored.
NOTE. The period of simulated failure should be sufficient for the purpose of the test (15 mins per light) whilst minimising damage to the system components e.g. lamps. During this period, all luminaire's and signs shall be checked to ensure that they are present, clean and functioning correctly.
Carry out the inspection and testing as described in the monthly test schedule, but mains failure test duration to be one third of rated duration time (usually 1 hour).
Check that upon restoring mains supply, all supply healthy indicators are again illuminated
Each luminaire and internally illuminated sign shall be tested as per monthly test but for its full rated duration in accordance with the manufacturer's information;